BACnet "Commandable with priority array"
Our Belimo Energy Valve requires a special mode for updating the setpoint. Regular writes fail. I tried selecting a Priority (instead of "Not Specified"), but that was not sufficient.
Belimo BACnet interface description
Belimo EDE file
Any tips for how to configure AO correctly in Mervis?
(Updating setpoint with the valve in Modbus mode works as expected, but they have not exposed some readonly-values that we need through Modbus.)
AVsetula administrators last edited by AVsetula
This bug where it is not possible to write a value from the PLC to the connected device appeared in some versions of the Mervis IDE, but we have always fixed it with the release of a newer version of the IDE.
It is currently functional in all Mervis IDE versions supporting BACnet:
- Mervis IDE 2.3.0 (106337)
- Mervis IDE 2.4.0 (117845)
- Mervis IDE 2.4.1 (125493)